Overflow - Pool Guide & Filtration Instructions
OVERFLOW POOL/ VANISHING EDGE
|Normal Filtration||Filtration||Closed||Open||Closed||Open||Closed||6-8 hrs Summer / 2-4 hrs Winter|
|Vacuuming Pool||Filtration||Closed||Partially Open||Open||Open||Closed|
|Backwash||Backwash||Open||Open||Closed||Closed||Open||Approx. 1 min|
|Rinse||Rinse||Open||Open||Closed||Closed||Open||Approx 30 sec|
|To empty Pool||Waste||Open||Closed||Closed||Closed||Open||Until Pool is emptied - Do not run pump dry|
|To empty Balance Tank||Waste||Closed||Open||Closed||Closed||Open||Until Balance Tank is emptied - Do not run pump dry|
|Internal Circulation||Filtration||Open||Closed||Closed||Open||Closed||When pool is filtered internally|
Ball Valves: Sump Closed
Balance tank Open
Multiport on filtration mode.
Performed when pressure gauge rises by .5Kg/cm or 7Psi above marked pressure. Switch off pump-turn multiport to backwash mode. Open waste ball valve Start pump and wait until sight glass in multiport clears. (Apr.after 1 minute).Switch off pump and turn multiport to filtration mode to re-start. Close waste ball valve.
Use same procedure but with multiport in rinse mode after every 2 backwashes for approx. 30 seconds to rinse filter.
Submerge vacuum cleaner in pool close to vac point. Prime vacuum hose and fit into vac point. Partially close balance tank ball valve and open vac point ball valve.
Vacuum pool slowly.
When cleaning is complete, switch off pump, open balance tank ball valve, dismantle vacuum and re-start pump.
Cleaning Pump Strainer
Switch off pump-multiport on closed mode, close all ball valves, open pump lid, empty and replace strainer, close lid firmly and open ball valves. Resume filtration.
Switch off pump and close ball valves, close dosing gauge 2 minutes prior to opening, open cover by pressing tab and turning anti-clockwise, refill chlorinator with required tablet amount, close lid and return to filtration mode.
Always turn off pumps when changing from one mode to another on multiport and when opening or closing ball valves.
Balance tank ball valve partially open
Vac point open
Multiport valve on filtration mode
Chlorine level should be kept between 1 - 1.5 ppm without a pool ionizer system and 0.5 ppm with such a system installed.
PH level must be kept between 7.2 - 7.6. PH Minus or Acid is required if ph value is above 7.6 and PH plus or soda ash / alkali granules must be added if value is below 7.2.
Clear tabs / clarifiers can be added to remove very small particles suspended in pool water.
Shock dose with chlorine granules once monthly.
NEVER DOSE CHEMICALS DIRECTLY INTO POOL . ALWAYS FILL BUCKET WITH WATER , ADD CHEMICAL AND DISSOLVE BEFORE DOSING POOL.
NEVER MIX CHEMICALS TOGETHER. DOSE ONE AT A TIME.